These cookies are necessary for the basic functions of the shop.
"Allow all cookies" cookie
"Decline all cookies" cookie
These cookies are used to make the shopping experience even more appealing, for example for the recognition of the visitor.
Statistics & Tracking
Track device being used
Order number: 7000531
Prices are only visible after login.
Availability: Ready to ship today, Delivery time appr. 1-3 workdays
Part No. 92743 Product Information Flexible compact DALI solution... more
Product information "BEG LUXOMAT?net PD4-M-DAA4G-AP"
Part No. 92743
- Flexible compact DALI solution designed for conference rooms, training rooms and classrooms
- High-sensitivity occupancy detector with the capability to address up to 64 DALI electronic ballasts (ECG)
- automatically, with segmented control via 4 groups
- Quick commissioning and maintenance processes via Smartphone/Tablet App (Android, iOS) - No PC-Tool required
- 3 lighting zones:
- A for main lighting with segmented constant light regulation via 3 DALI groups and offset control,
- B for lectern or blackboard lighting via separate DALI group,
- C for lectern or blackboard lighting by integrated relay
- Powerful switching relay for different operating modes, e.g. Cut-off function for DALI ballasts, HVAC, blackboard illumination.
- Manual switching or dimming via conventional pushbuttons
- Detection area can be extended with up to four Slave devices of type PD4-S-DAA4G
- Complete range of functions can only be activated using the B.E.G. IR-Adapter and a compatible Smartphone or Tablet (Android, iOS).
- Typical applications: conference rooms, offices, schools, universities
110 - 240 V AC 50 / 60 Hz
SM= Ø 124 x 85 mm
FC= Ø 117 x 100 mm
approx. 0.4 W
max. Ø 24 m across
max. Ø 8 m towards
max. Ø 6.4 m seated
Monitored area (tangential movement):
450 m² / 2.5 m Mounting height
2 m / 10 m / 2.5 m
Degree / class of protection:
SM= IP20 / Class II
FC= IP20 / Class II
-25 °C to +50 °C
DALI Control DALI output:
up to 64 DALI / DSI-EB , groupable in three DALI groups plus blackboard illumination or HVAC control
1 min - 150 min (Light zones)
10 - 30 % / OFF / 5 min - 60 min / ∞
Brightness set value:
10 - 2000 Lux
Relay (dry NO) Switching power: 2300 W, cos φ = 1
1150 VA, cos φ = 0.5
300 W LED
5 s - 120 min (HVAC)
Mixed light measuring
Related links to "BEG LUXOMAT?net PD4-M-DAA4G-AP"